Antifreeze: Does your process chiller need antifreeze? Maybe not....
Dow antifreeze - click here...Pricing & Availability 856-235-2120
* Since your chiller is tower water cooled and located indoors, your need for freeze protection is unnecessary (for ambient reasons only). Although all chilled water systems, (closed loop or evaporative), need chemical treatment of some type. If you presently use a chemical treatment company, please have the closed loop water system checked periodically. If you do not use a chemical treatment company, please let us know and we can direct you to a reputable company in your geographic area.
* Because your chilled water temperatures are always above 50F, freeze protection, due to the temperatures you want your water, is probably not needed. Although all chilled water systems, (closed loop or evaporative), need chemical treatment of some type. If you presently use a chemical treatment company, please have the closed loop water system checked periodically. If you do not use a chemical treatment company, please let us know and we can direct you to a reputable company in your geographic area.
* Since your product does not come in direct contact with your chilled water and not used in pharmaceutical or food production, you can use any type of industrial antifreeze. Although the EPA in your geographic area may "suggest" some type of propylene glycol. If that is the case, we recommend the Dowfrost-HD since it is a propylene glycol and had inhibitors to keep the plumbing lines and water in good condition.
* Since your chilled water loop has minimal losses, the need for a pre-mix solution is not as important. I would recommend that you have a pre-mixed drum of antifreeze and water (5 gallon cans or the like), available for that 3rd shift worker that might just refill your chiller system with water if a break in the line occurs. I also recommend if filters on the chilled water loop are checked, to have a 5 gallon bucket located at the filter area. This will reduce spills and keep the antifreeze in your system, not down the drain.
Chiller Warranty Service- Click here for details
The first hands on Chiller/HVAC/R troubleshooting handbook is out in publication. This is a must have book for you and your service technicians. It will save you time and money along with passing on the vast knowledge of 60 years experience.
This page was last updated on January 15, 2015
Click on any of the following hyper linked topics- especially if your browser does not support the java navigation bar above.
Chiller technical support for, plastics chillers, printing chillers, oem chillers, MRI chillers, laser chillers, air dryers,, hvac chillers
Chiller sales for,, chiller rental, used process chillers 2-20 ton, used process chillers 25-80 ton, used chillers 90-350 ton, rental chiller 8-80 ton, rental chiler 100-400 tons
About John C Schaub Inc,, chiller service, rates and hours, geographic chiller service regions, customer references
What is a chiller, chiller refrigeration cycle, chiller tonnage equations, chiller tonnage design parameters, size a chiller, chiller sizing
Chiller antifreeze info,, dowtherm, dowfrost, freezepoint mixture, chiller phone support, chiller water treatment, chiller water flow rates, emergency chiller service
This site was created and maintained by Jack Schaub
|Any inquiries please E-mail the Webmaster: email@example.com|
|John C. Schaub Inc. (On line 11/96) 23 Adams Street Mt. laurel NJ. 08054 phone 856-235-2120|